Buy Gefran PID Temperature Controller, 96 x 48 (1/8 DIN)mm, 2 Output Relay, V ac, V ac Supply Voltage ON/OFF RR Browse our. setting up the Gefran controller for the application referenced above. Additional software and hardware configuration information can be found in the User’s. Gefran controllers are built with SMT technology. The instrument provides a complete operator interface, protected by a Lexan® membrane that ensures.
|Published (Last):||14 September 2009|
|PDF File Size:||8.58 Mb|
|ePub File Size:||10.92 Mb|
|Price:||Free* [*Free Regsitration Required]|
The functions of each output are freely configurable from the faceplate.
Gefran 1200 Instructions For Use Manual
Level 1 Display Menu The functions of each output are freely configurable from the faceplate. It does not engage if the oscillations drop below 1. In this way, you just have to set the setpoint and the alarm, then launch self-tuning with the specific button. It can be one of two types: N disabled disabled disabled enabled disabled disabled Select number of enabled alarms disabled enabled disabled enabled enabled disabled disabled disabled enabled enabled disabled enabled disabled enabled enabled enabled enabled enabled By adding the following figures to the value in the table it is possible to enable a series of supplementary functions: The instrument can also select the parameters to be displayed based on its hardware configuration, which automatically hides irrelevant parameters.
Alarm 1 Alarm 2 Alarm 3 AL. InP Input settings third menu to set up This menu makes it possible to configure the parameters for the Controller input signals.
Gefran PID Temperature Controller | Thermon Africa
The instrument’s entire programming procedure is made easier by grouping the parameters in function blocks CFG for control parameters, Inp for inputs, Out for outputs, etc. Guide Modbus It is particularly in combined Heat-Cool control applications where the advanced algorithms come into play, allowing an extremely narrow band between heating and cooling without causing overlap.
In this way, you just have to set the setpoint and the alarm, then launch self-tuning with the specific button. S Format Decimal point position for input xxxx dP.
Enhanced software and hardware allow a high degree of user configurability. Keep to return immediately to level 1. Navigating Through The Controller Menu Navigating through the Controller Menu Keep pressed down to scroll through the menus in sequence and release it when the required menu appears.
The instrument can also select the parameters to be displayed based on its hardware configuration, which automatically hides irrelevant parameters. For more information click here. If the Integral Time value is too long Weak integral actiondeviation between the controlled variable and the set- point may persist.
GEFRAN INSTRUCTIONS FOR USE MANUAL Pdf Download.
Display Modification SP, alarms SP, alarms SP, alarms By adding the following amounts to 1200 values shown in the table a series of supplementary functions can be enabled: This manual also for: By tuning the three parameters in the PID controller algorithm, the controller can provide control action designed for specific process requirements.
Acquisition of the input signal msec.
Operator Interface Lexan that guarantees IP65 level protection. Below is a list of tags that have been applied to this product. R Digital from serial line Absolute Def. Integral heating time [0. Complete operator interface, protected by Gegran membrane to guarantee an IP65 faceplate protection level. The instrument is supplied with an “EASY” configuration calling for just a few parameters only those pertaining to the model ordered and essential to the controller’s operation.
Page of 40 Go. Heat-Cool Control Application example: During the test, 2100 the display segments and the 7 indicator lights will flash.
Lexan that guarantees IP65 level protection. An analog output in voltage or in current is also available.
Page 23 InP Input settings third menu to set up This menu makes it possible to configure the parameters for the Controller input signals. Documentation – Previous versions. It is enabled by means of configuration code AL.
The instrument is supplied with an “EASY” configuration calling for just a few parameters only those pertaining to the model ordered and essential to the controller’s operation. The purpose of a temperature control loop is to maintain the process temperature accurately at a determined level. Advice for correct installation. It is therefore an essential requirement for programming and configuring the controllers correctly.