The UMC documentation is split into the following manuals. UMC Technical Manual (2CDC D02xx)1. This is the main technical description. ABB’s new UMC offers you the optimal solution for your motor control center .. Please refer to the product manual for more detailed information. min. 3 W. Universal motor controller from ABB ABB’s new UMCFBP offers you the optimal solution. . They meet all the specifications of the respective fieldbus.
|Published (Last):||8 August 2005|
|PDF File Size:||20.42 Mb|
|ePub File Size:||5.27 Mb|
|Price:||Free* [*Free Regsitration Required]|
Registration Forgot your password? It can be used in three- and single phase operation mode. You only need to read the parts that are relevant for your application. Connect the Adr terminal to 24V DC at the second module. Voltage and Power Protection Functions This section describes the voltage based motor protection functions. Page Protection of frequency converters is not allowed. The UMC is designed for protection and control of three phase motors default operation mode.
UMCFBP Technical Presentation – ppt video online download
Mqnual fill in required fields. The function detects loss of suction for pumps, broken belt for conveyors, loss of airflow for fans, broken tools for machines etc. Motor Wiring U M C 1 0 0. Connecting more than one expansion module To connect several expansion modules to the UMC If the UMC is switched off the fault history is cleared.
The measured values are available on the LCD, fieldbus and function block editor. Nanual modules allow you to increase the number of inputs and outputs.
ABB UMC100.3 Manual
ABB UMC MANUAL Pdf Download.
Any reproduction, agb regard to purchase orders, the agreed closure to third parties or utilization of its particulars shall prevail. Contact information What would you like to do?
Events Customer events Investor events Media events. Hardware error of module Yellow: Table of Contents Add manjal my manuals Add. Check the configuration The menu option “Changed parameters” Got it, continue to print.
Protection of frequency converters is not allowed. A very stable bus com- munication even at high baud rates is the result! Learn more I agree. If within one second two low voltage situations occur, immediately after the start of the second umc1000 voltage situation the contactors are switched off. It is possible to mount the module separately from the UMC We think you have liked this presentation.